My key question is this, I installed the lights that are commanding GU10 LED in the ceiling in one of the divisions dual controls that turn on and turn off the lights in two different places commands in this room, where the micro module suitable for use in this situation ?
What kind of switches you have?
To use micro module you must place it at the switch where the LEDs are connect to.
For normal switch you must use 2267HE. In this case you can only use one switch! Second switch you must use scene module behind second switch!
For momentary switch (normal open) you must use 2267DHE. In this case you can use more then one switch parallel.
Another question I have is four shades, all with dual controls, which have two buttons one for stop and go up and down and makes another stop, there is a micro module suitable for use in these controls? or have to change the controls?
Do you have 2 button (Up/Down) or 3 button (UP/STOP/DOWN).
Nevertheless you can only have 2 terminals for the motor!
You can use 3160MHI.
For wiring see this document: Installationsanleitung PLCBUS-3160MHI
For further information about PLC-BUS have a look to this document: PLCBUS technical document